62 results Your Electric keeps the Crabtree Loadstar in three phase and single phase distribution boards in stock complete with B, C type MCB’s and RCBO’s. A Crabtree Loadstar triple pole, type D, 16A miniature circuit breaker will fit a Crabtree Loadstar distribution board. Fully safe this MCB has been manufactured . Crabtree Loadstar 6HS16B MCB; Rated Current: 16 Amp; Trip Unit Characteristic : Type B; Rated Operational Voltage: V AC; Breaking Current: 6 kA.
|Published (Last):||24 July 2016|
|PDF File Size:||3.26 Mb|
|ePub File Size:||10.24 Mb|
|Price:||Free* [*Free Regsitration Required]|
If it does not trip, the fault is with the wiring. The cable runs are enclosed in plastic trunking so it should not be affected by vermin!!!! Agree it won’t is highly unlikely! It has come to our attention that a very small number of Electrium Miniature Circuit Breakers, sold under the brand names Wylex, Crabtree Loadstar only and Volex, are not performing to the required characteristics.
Similar switchgear is switchgear that is used for the same fundamental application ie. The consumer unit enclosure must be manufactured from a non. Typical cabinets are meter cabinets that are normally built. All other devices are unaffected.
Crabtree Loadstar Amp Main Switch Disconnector a Double Pole SW2 | eBay
You would spend more lucrative time just visually inspecting all your garden stuff. What about Cable Entry?
Alun TomApr 26, What are Domestic Household Premises? The circuit is just one twin and earth going directly from mcb to a twin 13a socket which has now been disconnected! Alun Tom and unphased like this. Now only the 2. I am still intrigued as to why it is knocking off the RCB as absolutely nothing has touched the cable and the run from the cu to the the adjoining shed is all indoors. This can lead to a potential risk of burning, crabyree a small number of installations. To do this you would also need to remove the neutral of the suspect circuit.
Crabtree Loadstar 8 Way Distribution Board 125A TP&N Meter Ready
Crabtree Loadstar consumer unit. Does not see daylight! What is an Enclosure? As other poster loqdstar that aint the neutral bar it is the LIVE busbar.
OP have you tried to remove the breaker? TBH I think you are better getting someone in for this.
Welcome to Electrika Website
Garages,Workshops and Detached Summerhouses etc. Loadstar all metal cased. Yes I have thought of it but discounted that as a cause!! For the MCB to be the cause, there would have to be a path for the lost current to take. Log in or Sign up. And don’t forget that just switching off the MCB does not fully isolate the circuit. Share This Page Tweet. The screw is already loose. The crxbtree will not move Clip pulled down but no movement on this mcb or on other individual mcb if trying loadsrar to remove even with bus bar screw released.
Again thank you all for your help.
loadsyar There are many types of non combustible material however. Disconnected both sockets from junction box. Similar switchgear is switchgear that is used for the same.
Crabtree Loadstar RCD 80 Amp 30ma Double Pole 80a RCCB 18r80/30/2 | eBay
The ends of the supply wire temporarily terminated by a choc box connector At present still tripping in that state but yesterday when reconnected to the socket worked for approximately 6 hours without tripping anything then mid evening I now need to replace a suspect mcb Looking at the photographs of the cu can you tell me if I need to undo the bottom screw of every mcb in that sector to take off the copper neutral bus bar before I can take out the suspect mcb by pulling down the back release ring on the mcb etc.
RCD trip due to there being a difference in the current going out through the live and the current returning through the Neutral. Switch the circuit off, and inspect all the termination points at the different accessory positions. Not likely to be mcb at fault. Typical cabinets are meter cabinets that are normally built into the fabric of the building. Have you had any little furry visitors having a chew at the cable?
Alun TomApr 25, As usual good workmanship and proper materials should. If you have purchased or installed any of the product listed above, between the dates shown please visit our dedicated web page for assistance: I will now get an expert in and see what can be found.
Typical Domestic household premises would include single and. Today checked again and this time mcb did not trip rcd when switched back on. Else, yes, just drop the busbar, lift out the mcb, drop new one in and refit busbar.